Question about Heating & Cooling
Home AC furnace hums. Las tweak it wasn't working but still humming. 7 days later I works fine but it still hums. What coil be the problem from it working intermittently ? P.S. last week It did blow a 3 amp fuse but even after I replaced it it took a week for I to work again.
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
3 amp is standard.the fuse is blowing to protect the transformer.It is telling you that there is a short in the low voltage wiring.Goodman also had an issue with the coil shorting on the contactor.To prevent damage.....i'd call a pro.It should be a fairly simple repair.
Posted on Jul 04, 2008
There is a short in the low voltage wires somewhere for sure. The most common place is the low voltage on the outside unit, sometimes animals chew through them or they get cut with a weed eater. Just my experience. You basically have to trace it back all the way to the thermostat and heater. The only other thing is the contactor
Posted on Jul 01, 2012
Tips for a great answer:
Apr 19, 2016 | Heating & Cooling
Jul 24, 2013 | Cars & Trucks
Aug 08, 2012 | Ruud Matching Split Air Conditioner
Oct 04, 2011 | Bose Acoustimass 15 System
Jul 05, 2011 | Heating & Cooling
Oct 14, 2010 | Heating & Cooling
Jun 03, 2017 | Heating & Cooling
Nov 18, 2007 | Onkyo HT-SR800 System
Oct 20, 2017 | Heating & Cooling
171 people viewed this question
Usually answered in minutes!