Question about LG LS-L1210CL Mini Split Air Conditioner
Air con 24,000 btu mini split keeps giving me a e-1 error code.what does that mean
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
On a heat pump the difference from heat to cool is the reversing valve.
In cooling or heating the Y1 terminal will always be energized, this is the contactor.
Depending on brand the reversing valve will either be energized in Heat or Cool. At the outdoor unit check to see if the reversing valve is getting 24 volts in cool, if not check to see if it is getting 24 volts in heating. The easiest way to check if the reversing valve is shifting, is to feel the big copper tube, (it is not the suction line on a heat pump) this is a refrigerant vapor line. It will be cold in cooling and hot in heating.
Check your thermostat installation instructions and heat pump installation instructions to determine the proper terminal designations for your heat pump and thermostat. There are some brands out there that use the B terminal as common to the 24 volt circuit, so you have to check the wiring and make sure this is not common.
If it is energized in Cool then the Y1 and O terminal will be energized. You will have 24 volts from common usually the C terminal to Y1 and O.
If it’s energized in Heat then the Y1 and B terminal should be energized. You will have 24 volts from common usually the C terminal to Y1 and B.
If you get heat when you’re calling for cooling or vice versa then switch the wire between the B and O terminals.
Posted on Feb 10, 2010
SOURCE: We have LG air con
CH 33 -Excessive rise of standard compressor discharge temperature. If over 105°C check refrigerant charge. Over charged, release little gas still to normal PSI. If condenser full of debris, clean it.
Posted on Jan 01, 2011
E-5 -Comms Error, check your wiring, remove external pumps. Split/Multi - check volts from terminal N to 3 = 0 - 65 Vdc, Multi V - 4 Vdc terminals 3 and 4
Posted on Jan 03, 2011
SOURCE: Hi my LG healthplus inverter
Indoor Pipe Sensor or Outdoor Sensor Assy fault, Open or Short. Disconnect from PCB and measure resistance. Air sensor = 10 kOhm at 25C, Pipe sensor = 5
kOhm at 25C. If not replace sensor
Posted on Jan 20, 2011
SOURCE: what does the error code
could not find the error code but I did find a manual, hope it helps Tim:
Posted on Apr 27, 2011
Tips for a great answer:
Mar 22, 2016 | Sanyo 12000 Btu Mini Split Air Conditioner...
Oct 08, 2015 | LG 18000 BTU Dual Zone Mini-Split Heat...
Nov 14, 2014 | Samsung AQV09JA Classic Wall Mounted Mini...
Jul 25, 2014 | Fujitsu HALCYON AOU24CL1 Mini Split...
Jun 17, 2014 | Ingram's Water and Air ComfortStar Mini...
May 04, 2014 | LG LS-K1830CL Cool Mini Split Air...
Sep 18, 2013 | Whirlpool Heating & Cooling
Dec 11, 2010 | AmcorAire UCHW-H12AF2 Split System Air...
236 people viewed this question
Usually answered in minutes!