Question about Danby DPAC10031 Air Conditioner
The unit filled with water in dehumidifier mode. We emptied the water but the red indicator light will not turn off and therefore the unit will not do anything but fan. Yes I turned it off and waited a minute and turned it on again. There is no button for clear or around the red light. Thank you very much in advance. Val
Check to make sure your fill bucket is correctly placed back into the unit. there is a safely switch that will not let the unit work without the bucket in place..hope this helps let me know?
Posted on Aug 24, 2007
I am having same problem please tell mw which side you cleared from water because i do not see any other place for water
Posted on Jun 22, 2008
I have the APAC8040 model (danby arcticaire unit) and the red "water full" light was flashing even after i'd emptied the external tank. reading the post above helped; i'd never realized that i could access and remove the internal tank to empty it as well. it's located on the side of the unit (bottom right side, when looking at the unit from the front). drained that tank and the red "water full" light went out and the A/C is working again. yay!
Posted on Jul 05, 2009
Tips for a great answer:
When the STOP indicator light turns on, the internal water tank has filled with condensed water and the air conditioner will turn off automatically. You can drain the internal water tank by removing the plug on the back of the unit, be ready for a lot of water to come out of the unit. The unit will shut down when the water pan is full. This condition may occur either when the unit is operated in high humidity conditions, or when the unit is being operated in HEATMODE, since the auto-evaporation function will not work in the heating mode. I hope this helps, have a great day, Andy K.
May 22, 2013 | Air Conditioners
Aug 03, 2011 | Haier CPRD12XC7 Air Conditioner
Jun 08, 2011 | Danby DPAC12030 Air Conditioner
Jun 08, 2011 | Air Conditioners
Jul 13, 2010 | Danby Air Conditioners
Aug 21, 2009 | Amana Portable Air Conditioner
Aug 20, 2009 | Air Conditioners
Jul 18, 2009 | Amana Air Conditioners
Nov 18, 2007 | Danby DPAC10031 Air Conditioner
1,626 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: