Question about Goodman CLQ36AR49 Air Conditioner
I have a goodman heat/ac unit that is leaking water from the unit. Any ideas what this is or how to fix it? I am a single mom that lives in florida and cant afford to repair man and have had to turn the a/c off!
The problem maybe the same I am having. I have condensation forming under the drain pan do to the temp. difference from the cold water on top and the warmer air below the pan. To correct this I installed fiberglass insulation under the entire pan to keep the temp. Constant. This will prevent warm air contacting the bottom of the pan causing it to sweat. Chris email@example.com
Posted on Aug 22, 2007
I suppose that the water is coming from the unit where the blower motor is. Condensation is created by the evaporator coil while its running and is suppose to drain into a pan under it and through a pipe to the outside. This pipe could be stopped up. The easiest way to fix that is to blow air through the pipe from the outside. It probably comes out close to the outside unit. It could be that your inside filter is dirty causing reduced air flow and making the evaporator freeze too. Change the filter. That may help. There are other steps that you could take if these don't help. Contact me by email if you need to. Cant run over there because I'm in Missouri but may be able to help in a chat room. firstname.lastname@example.org
Posted on Aug 16, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jun 13, 2015 | Goodman Heating & Cooling
May 29, 2014 | Goodman Manufacturing GSZ130181A - 1.5 Ton...
Aug 10, 2012 | Goodman Heating & Cooling
Aug 19, 2011 | Goodman CLQ36AR49 Air Conditioner
May 16, 2011 | Goodman CKL42AR42 Air Conditioner
Apr 28, 2011 | Goodman Heating & Cooling
Aug 11, 2010 | Goodman Heating & Cooling
Aug 30, 2009 | Goodman CLJ30AR32 Air Conditioner
298 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: