Re: furnace will not light, but there is gas to the house
This problem will need to broken down in several steps. First, reset all the breakers that operate the furnace and ac. Turn the thermostat to on and the ac to off and see if the furnace blower starts. Get back with me.
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
The AC unit outdoors must be running and rejecting heat by its air flowing through it the 2 copper lines are the refrigerant lines, the fatter one should be "beer can cold" if not its low on refrigerant or not running.
When it blows cold air, there should be an error code blinking on the LED light located on the PC board. Look through a small viewing port in the front panel, then remove the front panel and on the reverse side there should be a diagnostic code chart to help you figure what is wrong.
Heat pumps provide good heat until the tempurature drops below 35-40 degrees. After that there isn't much heat to extract from the outside air and then either the gas furnace kicks in or the electric heat strip does the job of heating the air. if you have heat strips, I would check your breakers in your panel and sometimes there are a couple of breakers right on the air handler or furnace. The ones that will be for your heat strip are 220v and will be twice as wide as your normal 110v breakers . Please don't trust a visual inspection as they can look like they are in the "on" position but are indeed tripped. Turn them all they way off and then back on. If the beakers check out you may have an open cicuit in the heat strips themselves and you will need to have a qualified HVAC tech look at your furnace to repair it.
If your furnace is a "duel fuel" and uses natural or LP gas for back up heat then your ten year old rheem probably needs a good maintenance by a qualified service tech. There is a flame sensor to clean, ignitor to check (replaces the old school pilots), burners to clean flue connections to check and much more. ALL manufacturers of any heating apliance recommend yearly maintenance. Most companies offer something for around 100 bucks. I hope this helps.
It sounds to me that your air flow is restricted somewhere. The first thing to check is your air filter. If that gets real dirty your restricted air flow will cause the hi-limit(hi temperature limit switch) in your heat exchanger compartment to over heat and open up your gas valve electrical circuit,thus, shutting off the gas to your burners. After the hi-limit switch cools down the furnace will go back to heating again then it will overheat again(you get the picture?) If it keeps cycling on and off like that the house will never get warm if it is cold outside. If your air filter is reasonably clean(you should be able to see light thru it easily) then the secondary heat exchanger could also be dirty, this is located above the indoor fan housing, you would need to pull the indoor blower assembly out of the furnace and look up above. The secondary heat exchanger looks similar to a radiator will fins. You can use a medium stiff plastic brush to brush the dirt,hair, whatever off of it. Another problem spot would be the cooling evaporator coil (if you have central airconditioning) located most likely above the furnace in the plenum(if your furnace is in a basement). This usually is difficult to access if an access cover wasn't installed when the airconditioning was installed. I would recommend an experience service tech to clean it for you. Also make sure all you supply air registers and return air registers are open . These are the things I would check first. Good luck!!
This is a little complicated because it can be several things and you need to provide more specific info....It could be your furnace is shutting off on the High Limit...which means your furnace is running too hot...check the filter , return air vents etc would be an airflow problem...dirty blower....Furnace can be too big for your house....when the furnace shuts off on High LImit , the fan will continue to blow air , cooling it down as usual and once the furnace cools enough to reset the high limit trhe furnace will Ignite again as long as the thermostat is still calling for heat . The furnace could also be running too long and getting too hot....your Ductwork can be too small...many factors come into play
It is normal. Your house has to go down a couple more degrees because the heat pump is not working. You can solve this by rewirng you thermostat. Take off the wire that goes to Y and tape off. Then take the wires that are marked w and e or w1 and put the wires to yellow. Do not run ac with it wired like this. If you need more information please post me back
not familiar with that particular model but on virtually every type and style of furnace i have worked on in the last 21 years. the fan is delayed. usually the burner lights then 3 to 5 minutes later after the heat exchanger has gotten nice and hot the fan comes on and blows nice and hot air. on old furnaces there was and is a switch usually on the upper right side of the furnace bulkhead that has a spring like device that heats up and rotates till it makes a set of contacts that turn the fan on. if it gets to hot the set of contacts breaks the power to the gas valve and shuts down the burner. as the furnace cools down on shut off there is a third set of contacts that open to turn off the fan so you don't get a draft. sometimes the stat can be wired up wrong, and it will bring the fan on right away ,and air will be cool and drafty till furnace catches up.