Question about Ruud 3 Ton Split System Heat Pump
Turned on a/c has been running for about 4 hours but has not cooled the house-fan outside is not turning
Posted by Anonymous on
You have condenser issue. check at outside unit for 240 volts to contactor and 24 volts to contactor coil.
Posted on Aug 17, 2015
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
It sounds like the unit is tripping off from high pressure. Check you filter and indoor coil. You may have low air flow inside that is causing the refrigerant pressure to be to high.
Posted on Mar 22, 2009
first look for red button neer the copper line set if has one push it second inspect thermostat wires for weed eater damage check disconnect for fuses check breaker at main panel pull disconect and remove cover check stat wire connections look at the capacitor if swelled up on top bad if all look ok put disconect in using insulated object manually push in contactor if unit comes on check for 24 volt ac on yellow stat wire to common if none stat wire could be loose at indoor unit or stat bad hope this helps you
Posted on Jun 06, 2009
The buzzing sounds like the fan trying to start. Try a new fan capacitor, or get a new fan
Posted on Aug 07, 2012
Tips for a great answer:
Nov 29, 2013 | Rheem 3.5 Ton 14 Seer / Ruud 100K Btu 80%...
Aug 08, 2012 | Ruud Matching Split Air Conditioner
Aug 06, 2012 | Ruud UBHC Air Conditioner
Jun 18, 2011 | Ruud Heating & Cooling
Oct 23, 2008 | Ruud Heating & Cooling
Jul 02, 2008 | Amana PTH123B25AJ Heat Pump Air...
120 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: