Question about Goodman GMS90703BXA Heater
It were working perfectly well for about 6 months. Last winter, suddently stop. I called a technitian, he replace the 3 Amps fuse and the heating start working again. Later, same day, I try to turn on the fan, and the 3 Amps fuse, blow again. Can some one help me with this problems? Thanks.
It is a problem on your low voltage side. I had the same issue and found that my wire going to my outside condeser had been snagged on a wire hanger in my basement and was shorting out the system. I went a head and replaced the entire wire from my outside unit to my indoor and haven't had an issue since. So my advice is go to HD or Lowes and purchase some 14 gauge wire and replace the low voltage wire. If that doesn't work, then replace the thermistat wire, and thermistat. Great time to upgrate to a energy efficient thermastat.
Posted on Mar 18, 2009
This fuse is used on the low voltage side of the furnace. All 24 volt controls operate thru it. You may have a short in your thermostst, thermostat wire or even a bad transformer. After replacing the fuse, inspect the wiring in the cabinet as well as the wire heading toward the thermostat for damage. If you find none, check the thermostat for loose wires or contacts. If all else fails, jump out R and W with a small jumper temporarly at the furnace and see if the unit runs. You will have to tape the door switch closed to run it with the panel off. Remember, this will keep the furnace running 100% of the time until you disconnect the jumpers. Not a solution, just a test! If it runs flawless, you have a bad thermostat or wire. Diagnosing a transformer is for a technician.
Posted on Sep 18, 2007
I HAVE THE GMPN 0804 AND IT CAME ON THIS MORNING AND THEN A LOUD NOISE CAME OUT OF IT. I IMMEDIATELY SHUT OFF THE EMERGENCY SWITCH. AFTER A FEW MINUTES I TURNED IT BACK ON AND IT KICKED IN BUT THEN IT MADE A CLICK IN THE FAN ON THE BOTTOM WHICH DID NOT KICK IN AND SMELLED A LITTLE.
Posted on Oct 26, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 14, 2017 | Goodman GMS90703BXA Heater
Jan 27, 2018 | Goodman GMS90703BXA Heater
Nov 22, 2010 | Goodman GMS90703BXA Heater
Feb 13, 2010 | Goodman GMS90703BXA Heater
Dec 18, 2009 | Goodman GMS90703BXA Heater
Nov 17, 2008 | Goodman GMS90703BXA Heater
Jul 03, 2008 | Goodman CLQ36AR49 Air Conditioner
May 16, 2008 | Goodman GMS90703BXA Heater
Jan 04, 2008 | Goodman GMS90703BXA Heater
1,104 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: