Question about Heating & Cooling
Wall controller not responding, indoor / outdoor unit operating think cust has altered outdoor dip switches
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: outdoor not workin
the outdoor unit is totally dead or only to the heat mode?if it is to the heat mode propably must check the refrigirator.if it is too the cool mode the plate has problem.if is multi check the outdoor plate in other occasion check the indoor plate.
Posted on Mar 29, 2009
I'm not sure exactly what unit you have and what controls you have installed on the unit. But....there usually is a flash code schematic on the unit. Usually on the inside of the blower compartment cover. This should tell you what is wrong with the unit. It could have a low voltage short somewhere and is loosing the call for cool. So the answer can be a possible yes to your question but without knowing the flash code, it's hard to tell from my point of view. You might end up calling a service professional out to check it.
Posted on Mar 30, 2009
SOURCE: System will not start up.
This is a signal fault between the indoor and outdoor first make sure the dip switches are set start with the unit closest to the condensor set as unit 1 then next unit as 2 and so on the dip switches are inside the indoor unit on the pc board if you check the manual it will tell you which swithes to set, if this wasnt done when the units where installed they would have never worked i would also check the signal wiring between the wallmount and the splitter box / bc box and make sure there isnt a loose connection when you have ruled this out id say more than likely it is a faulty indoor board on the wallmounted unt
Posted on Apr 08, 2009
These units have circuit boards inside that have lights on them. These lights come on and tell you what the problem is. I have had 4 units do the same thing that yours is doing. The result has been that the compressor has gone bad. You have to get access to the control board to see the lights. There will either be one inside the inside unit or one inside the outside unit depending on exact manufacturer date.
Good luck and hope this helps.
Posted on Aug 23, 2009
Hi, the control voltage to both indoor and outdoor will always be 24 volts AC. If this is a heat-pump unit, the high voltage to the indoor and outdoor will be the same, 208/ 230/ 240/ 277. If it is a split unit with a gas fired unit, the outdoor will be 208 or higher and the indoor will be 120volts AC. I'm sorry, you have the inducer motor, so it is gas! My mistake. Yes, always the gas furnace will be 120 volts AC and the remote condenser will always be 208 and higher. As far as replacing the inducer motor with a different kind, it will have to be the same voltage, 120, and amps, R.P.M's, 60hz, and made to pressurize and be able to vent Hot gases also. It must fit and operate like the old one. They should make a replacement universal motor to fit? Check with some of the wholesale houses on this and they can locate a motor to fit. Keep me updated on this please Don.
Posted on Dec 19, 2009
Tips for a great answer:
Apr 19, 2017 | Samsung Heating & Cooling
Nov 15, 2016 | Fujitsu Heating & Cooling
Mar 11, 2015 | Daikin FTXS18HVJU Wall Mounted Indoor Unit...
Mar 06, 2015 | Heating & Cooling
Jul 21, 2014 | Daikin Mini Split Concealed Duct Units
Oct 05, 2011 | Frigidaire FAH125P2T Air Conditioner
Dec 29, 2010 | Heating & Cooling
Jul 11, 2010 | Fujitsu 24C1 Air Conditioner
Dec 18, 2009 | Hitachi Heating & Cooling
Jan 27, 2009 | Fujitsu 24C1 Air Conditioner
Sep 20, 2017 | Heating & Cooling
46 people viewed this question
Usually answered in minutes!