Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: ERROR CODE CH5 AIRCON SPLIT LG
This error is a communication error between your indoor and outdoor unit. You can try turning the breaker off for a few minutes and restart the unit. However if that does not work its best suggested to have an authorized HVAC technician service the unit.
Posted on Mar 12, 2010
SOURCE: my LG split system Model
It's communication error between indoor and out door. Make sure you have command from indoor by checking volts in out put of indoor or in put of out door. If not, Check your PCB and also loose connections.
Posted on Dec 19, 2010
CH-05-Comms Error, check your wiring, remove external pumps. Split/Multi - check volts from terminal N to 3 = 0 - 65 Vdc, Multi V - 4 Vdc terminals 3 and 4
Posted on Jan 01, 2011
E-5 -Comms Error, check your wiring, remove external pumps. Split/Multi - check volts from terminal N to 3 = 0 - 65 Vdc, Multi V - 4 Vdc terminals 3 and 4
Posted on Jan 03, 2011
Tips for a great answer:
Sep 29, 2013 | LG Heating & Cooling
Dec 19, 2010 | LG Heating & Cooling
Apr 17, 2010 | LG LS-L1210CL Mini Split Air Conditioner
Jan 18, 2010 | LG Heating & Cooling
Dec 24, 2009 | LG LS-L1210CL Mini Split Air Conditioner
Jan 14, 2009 | LG LSC183VMA Split System Air Conditioner
49 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: