Question about Heating & Cooling
Runs ok but cuts out on o/temp and rollout have to reset them runs ok for a while then cuts out again might run ok for 2-3 days
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If this is a hot water heating system for home heating It may be thermocouple of flame sensor. If it has a sensor rod in the flame check and make sure flame is hitting it. Also a little sand cloth to polish it may do the trick. I have to due this to my gas furnace sensor every couple of years. If this unit has a pilot light and it is weak and yellow verses strong and blue it may need cleaned. Some times you can tap on it while it is burning and it will dislodge plug. If it A domestic hot water heater for washing and such the above still holds true. If polit is strong and hitting thermocouple then replace thermocouple.
Posted on Jul 04, 2009
Error code CH61 - CONDENSER PIPE HIGH PRESSURE. This can be due to overcharging of the system or the condenser clogged with dust or an obstruction, or condenser fanmotor not working. Hope this helps.
Posted on Nov 18, 2009
burners could be rusted blocking gas from getting across , so it pockets up and ignites all at once ,there also could be a partial blockage in heat exchanger but this is unlikely, or more seriously the heatexchanger could be rusted out with large holes in it so when blower comes on the positive pressure pushes flame back. either way when the roll out switch is tripped it indicates a pretty serious and potentially harmful issue that should be inspected and diagnosed by a reputible company.
Posted on Dec 02, 2010
Tips for a great answer:
Feb 15, 2014 | Goodman Heating & Cooling
Jan 27, 2014 | Goodman GMS90703BXA Heater
Jun 04, 2012 | Pentair MiniMax 100 Aboveground 100,000...
Jan 05, 2011 | Goodman GMS90703BXA Heater
May 02, 2010 | Garden
Apr 30, 2010 | Heating & Cooling
May 12, 2009 | Heating & Cooling
Dec 13, 2008 | Goodman GMS90703BXA Heater
16 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: