Question about Electrical Supplies
I wired the generator to a two pole breaker box for two 120 volt circuits. I get 116 volt on each side at the box from the generator. Installed breakers and the first one register 116 volt (no wiring connected yet. Turn the second breaker on and voltage on the first drops to about 105 and the other one register about 135 volts (again no wiring attached. Have no clue where to go. All connections are good an tight. Help111
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: one half of a 240
The breaker must engage TWO bus bars in the panel, in addition to the a neutral connection. If the breaker is aligned to engage only one of the bus bars, only one of the terminals will be powered at the breaker terminal screw (most likely the top).
Some electrical panels have covers that have numbers and spaces stamped for circuit breakers at the bottom; when in reality, there is no bus bar to connect. Make sure you are not attempting to install into a space that lacks both bus bars.
If unable to get 240 volts out of the breaker without the load wires connected, there may be an issue internally with it. If after connecting the load wires, one side fails again, it may be detecting a ground fault or an over current situation but due to an internal failure is unable to trip both poles of the breaker. This breaker should be replaced.
Posted on Jun 02, 2011
Tips for a great answer:
Apr 25, 2015 | Frigidaire FAC126P1 wall/window Air...
Apr 16, 2014 | Electrical Supplies
Mar 15, 2014 | GE 20 Amp 1 In Double Pole Circuit Breaker...
Mar 10, 2014 | Electrical Supplies
Jan 30, 2013 | Electrical Supplies
Dec 01, 2012 | Coleman Cable Woods 59402 40Amp Timer for...
The voltage between Y and X should be 240-Volt, X and W
120-Volt, Y and W 120-Volt, X and G 120-volt, Y and G 120-volt, W and G
Hope this helps! Hal aka ImJustAvg
Jan 01, 2012 | Dryers
Sep 07, 2011 | Whirlpool Dryers
Jul 03, 2011 | Intermatic T104R 208-277Volt 40-amp Timer...
May 14, 2011 | Electrical Supplies
149 people viewed this question
Usually answered in minutes!