Question about Pentair Mastertemp Pool & Spa Heater Dual Electronic Ignition 400,000 Btu Lonox Propane 460737
Tested heater for this season (worked well end of last season). Heater ignites and runs from anywhere from 2 minutes to 15 minutes (depending on flow rate or if the universe is happy or not). Burner shuts off. Front panel shows "Service Heater" while rear of panel shows HLS error. After a couple of minutes, heater re-fires and burns for a while and same error LEDs. My flow rate is within the parameters for the heater. I am wondering if my HLS switch has gone bad. The switch is about $40 on Amazon, but not sure how to install (I'm OK with electronics, not so much with plumbing) or if this is the issue. Any advise more than welcome before I call a service tech.
Hello.... HLS usually means hi limits.... check the connectors at the high limit switches, to make sure they're not rusting off. If they're good, and the heater fires, but turns off after a minute or two, the problem lies usually with the temperature regulator.... it's the round cover with the 4 slits in it between the inlet and outlet. It comes out counter clockwise. It holds a spring with what would be a car thermostat attached to the end of the spring. That thermostat can be malfunctioning, and it will allow the water to get too hot coming out of the heater, which trips the hi limit. A quick fix is to remove the spring with the temperature regulator, and put the cap back in place. You definitely want to get another one to replace it, because the efficiency rating of the heater will go down considerably.... but it will do the job in the meantime with no danger. (Its like running a car with the thermostat removed, it can be done, but the engine runs too cool). They cost about 50 bucks on amazon.
Posted on Jun 21, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Low out put voltage from the pilot generator and/or an open circuit in the control circuit...the most common is a bad pressure switch (dirty filters can hamper pressure switch operation).
Posted on Jun 28, 2009
SOURCE: Pool heater will not heat
Im no pro, but I know there is an air sensor behind the main board. If the fan is running you probably have a problem with that sensor. If your lucky the air hose could have just popped off.
Posted on Apr 04, 2009
high limit is open this is due several factors like slow water .pump on low speed or dirty filter, also hard water, or assembly valve not working properly so make sure the filter is clean check the water chemistry an last check the valve assembly. make sure plumbing is correct water in and out from the heater
Posted on Sep 19, 2009
if none of the above don't work, put a brick on top of the vent, covering only about 1" of the vent, then try firing it up. if it works, then you aren't getting enough oxygen at the ignitor.
Posted on Aug 08, 2010
Tips for a great answer:
May 25, 2014 | Lochinvar ENERGY RITE 399000 BTU PROPANE...
Dec 26, 2010 | Rinnai Toyostove Direct Vent Heater:...
May 31, 2010 | Jandy Lite 2 Natural Gas Pilot Light...
May 25, 2010 | Raypak Free Hydraulic Lift Gate Delivery -...
Mar 10, 2010 | Raypak Free Hydraulic Lift Gate Delivery -...
Jan 09, 2010 | Sta Rite Sr333na Max E Therm Pool & Spa...
Aug 29, 2009 | Pentair Mastertemp Pool & Spa Heater Dual...
Jun 24, 2009 | Sta Rite Sta-Rite Max-E-Therm High...
212 people viewed this question
Usually answered in minutes!