Question about Goodman Heating & Cooling
One of the motor mounts on my ARUF032-00A-1B Goodman air handler are broken. Is there a fix or do I need to replace?
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: GOODMAN # ARUFO49 AIR HANDLER
MOST ALL GOODMAN ( UP TO 3 TONS)INTERNAL FILTERS ARE 22" x 22" X 1". YOU CAN GET THEM ON LINE AT www.filtera.com. ALWAYS TAKE A TAPE RULE AND OPEN THE BOTTOM FILTER DOOR AND MEASURE THE FILTER RACK. MAKE SURE YOU DO NOT HAVE A RETURN-AIR FILTER-GRILLE. LARGE WHOLE -HOUSE RETURN AIR VENT NEAR OR AT YOUR FURNACE, A/C AIR HANDLELER. Joe_Rex New Member of FixYA Retired HVAC&R contractor 45+ years exp.
Posted on Apr 28, 2007
I bought window AC (5000 btu) that fit 17 in. at home depot. made by Zenith. Keep in mind of your room size.
Posted on Jun 10, 2008
On your t-stat you have Y, W1, W2, R, O, G, B or C or X. Y is your cooling circuit and will be the same in the air handler and heat pump unit, use the yellow wire for this circuit. W1 and W2 are your back up elec. or gas heat. Depending on how many kws or heat strips you have and t-stat wires you will put the white wire to W1 in both the t-stat and air handler. W2 is for your second stage back up heat if air handler calls for it, this will be a tan or brown or black t-stat wire and goes to W2 on t-stat and air handler. R is half of your 24v control power from the transformer and is the red wire and goes to the t-stat, air handler, and heat pump. O is for the reversing valve in the heat pump that switches it from heating and cooling. You guessed it the orange wire connect to t-stat and heat pump. G is for the blower and is the green wire to the t-stat and air handler. B or C or X is known as the common which is the other half of control circuit from 24v transform it is the blue wire and goes to the t-stat, air handler, and heat pump.
Posted on Oct 09, 2008
Look at your Thermostat wiring.
If there is a green wire going to the "G" terminal, disconnect it.
If it stops running, you have a bad T-stat.
If it keeps running, you either have a stuck fan relay or a low voltage control wiring malfunction.
Those are usually related to one of the safety switches having problems.
If green is not going to G, let me know, and we will determine which one is indeed the fan wire and go from there.
Remember, when you rate the solution, it closes further dialog, so only rate when you are satisfied with the discusion.
Thanks for visiting FIXYA!
Posted on Jan 03, 2009
You may have dirty stopped up drain pan or drain. Take a dryvac and **** the drain from outside. This will clear all the drain. Is it cooling ok? Is the unit in an attic? The drain is not hard to clean. Check your coil(evap) inside to see if this is clean. Rus
Posted on Jul 11, 2009
Tips for a great answer:
Jul 20, 2014 | Goodman Heating & Cooling
May 20, 2014 | Goodman AWUF180516 Vertical Wall Mount,...
Feb 12, 2013 | Goodman Heating & Cooling
Jul 29, 2012 | Goodman Heating & Cooling
Oct 05, 2011 | Goodman CLQ36AR49 Air Conditioner
Jan 02, 2011 | Goodman CLJ30AR32 Air Conditioner
Oct 05, 2010 | Goodman Heating & Cooling
Oct 30, 2009 | Goodman CLQ36AR49 Air Conditioner
May 31, 2009 | Goodman CKL49AR49 Air Conditioner
51 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: