Question about Randell (84111NPCB)
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: I have a Randell 5ft
This unit uses Thermostat/Solenoid Valve Combination's to control the temperature
1. Rail 2. Bottom Storage
The way it works is the thermostat senses the need for cooling and energizes the solenoid valve. This allows refrigerant flow which cools the area it is controlling. Once the thermostat is satisfied the contacts open and the solenoid is de-energized closing the valve. If the solenoid is bad, the valve remains closed, no refrigerant flow, warm unit.
Test the solenoid coil (two wires) to see if voltage is present either with a volt meter, or remove the coil off the valve and place a screwdriver (insulated) through the coil hole and you should feel the pull like an electro-magnet (what a coil is).
Posted on Dec 05, 2010
Tips for a great answer:
Oct 07, 2014 | 1999 Oldsmobile Cutlass
Oct 02, 2011 | Randell Refrigeration 27'' Undercounter...
May 08, 2011 | Randell RAN-8383N Refrig Raised Rail Prep...
Mar 01, 2011 | Randell 9040K-7
May 17, 2017 | Randell Refrig Raised Rail Prep Table 60"L...
Dec 05, 2010 | Randell Refrigeration 60'' Refrigerated 2...
Jun 10, 2010 | Randell 2020FE Freezer
Jun 11, 2009 | Goodman CLQ36AR49 Air Conditioner
May 27, 2009 | Heating & Cooling
May 01, 2009 | Ruud UAMB Air Conditioner
Oct 21, 2010 | Randell (84111NPCB)
40 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: