Question about Heating & Cooling
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: need wiring diagram for a
go to this site. in the manual, there is a wiring diagram that may answer you question for a diagram. hope this helps.
Posted on Sep 15, 2010
SOURCE: Thermostat wiring from York air
For a competent expert to be able to answer your problem, you will need to givea specific make and model of your unit.
Also include as much as possible about what you have already tried to do toresolve the problem along with exactly what is not working or what the unit isnot doing that it is supposed to do.
This will help us experts to be able to give you the correct advise the firsttime, without having to guess so much as to what is actually happening.
Posted on Sep 27, 2010
SOURCE: i have a ckL 36-1L
Hi, I can tell you how to wire it, but no diagram. Take the common wire from the compressor, look on the terminal cover or straight at the terminals and you will see C, R, and S. Wire colors vary. C is common on the capacitor, R goes to herm on the capacitor, and S goes to the load side of the contactor, or outlet side, to one of the un- used terminals on either side of 220 volts. That takes care of compressor, R, Run, S, Start, and C, for Common. Low voltage wires will be 2 -18gauge wires coming off each side of the coil on the contactor, connected to the 2-wires coming from your indoor unit, 24 volts. Your off and running unless its off on low pressure switch, and then it will start when you start adding freon.I hope I have been of help to you.
Posted on Jun 03, 2011
Tips for a great answer:
Aug 06, 2014 | Heating & Cooling
Nov 12, 2013 | Heating & Cooling
Feb 22, 2012 | Heating & Cooling
Mar 02, 2011 | Ruud Matching Split Air Conditioner
Sep 27, 2010 | Heating & Cooling
Sep 15, 2010 | Heating & Cooling
Sep 05, 2009 | York Yankees Bedding MLB Comforter
Jul 10, 2009 | York Yankees Bedding MLB Comforter
Apr 26, 2009 | Heating & Cooling
110 people viewed this question
Usually answered in minutes!