Question about Raypak Rp2100 Digital 336k Btu Propane Heater
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: pool heater wont fire up
Its just after 1 am here as well, Ontario Canada. Yes, you have to remove the front lower panel by raising it then pulling out at the bottom. Then compare the valve you have with the 2 in the picture on pg 5. If it is easier, you can have your husband call me while doing this and I can talk him through it. My contact information is located on the main page of my company website www.emshvac.com
Posted on Jun 23, 2009
you are in fireman switch mode,which means pool timer is ready to shut down pump. clk shuts down heater approx 15 minutes before pump shuts down. this lets heater cool down before pump shuts off.
Posted on Jul 23, 2009
this usually indicates a high limit condition.you must first ascertain if you have a component failure or a true high tempature condition.your model has 2 limit controls and they are both located in side panel on water in/out header
Posted on Sep 19, 2009
For some reason your heater is not recognising the flame when it goes on. The biggest reason for this will be small spider webs in the burner orfaces. These are on the main gas manifold where it connects to the burners. You can get a small wire and bend it to go in these orfaces but the first time you do this it will probally be easer to pull the tray and remove the orfaces from the gas line. Good luck, I hope this helps.
Posted on Nov 28, 2009
Thank you for posting your question here on Fixya.com.
Replacing the roll out switch is an easy do-it-yourself repair. Fixing the problem causing the roll out of the burner flames in the first place is a bit more of a pro job. Something is causing to much heat to roll out the the combustion chamber into the control area causing the switch to fail. You will continue to burn the link until the underlying problem is fixed.
If this answer does not fix your problem, please comment with additional details prior to rating the answer. Positive feedback is appreciated once your problem is solved!
Posted on Jun 01, 2010
Tips for a great answer:
May 27, 2016 | RAYPAK R266A 266K BTU ASME DIGITAL...
Feb 03, 2015 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Aug 17, 2014 | Raypak Pool & Spa
Jul 16, 2014 | Raypak 130,000 BTU Natural Gas Pool...
Jun 05, 2014 | Raypak RP2100 DIGITAL POOL HEATER R206...
May 29, 2014 | Raypak Free Hydraulic Lift Gate Delivery -...
May 05, 2014 | Raypak Pool & Spa
59 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: