Question about Heating & Cooling
Outside unit will come on for a few secone and then trips breaker in main breaker box. What should I look for?
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Check your wiring between the contactor and compressor for a short to ground, or check the compressor windings for short to ground.
With the Tstat off, the contactor should be open so the only way for the compressor to be trying to do anything is if the 110 volts from the unbroken side are traveling through the compressor to ground. Since 110v is not enough to run it, the overload is kicking it out, cooling off, and repeating the cycle. When you kick on the Tstat, the contactor is supplying voltage directly to ground without going through the resistence of the compressor windings and kicking the breaker.
Post back and let me know what you find.
Posted on Nov 20, 2007
If your outside condenser has a locked rotor or short circuit, than the unit WILL trip the breaker - as it should. On the other hand if a breaker is tripped a few times it will have less of a capacity that the rating, (this is designed in it). You will need to determine if the unit is locked (and broken) or the breaker has become too sensitive.
Posted on Apr 22, 2008
Possible low voltage condition would cause that kind of a problem. To small a cord without the ability to carry and maintain the voltage would cause a voltage drop. I would test the voltage supply and make sure it is within 10% of that required for your A/C to operate properly.
Posted on Jun 16, 2008
Clicking sound is the contactor engaging to start the outside unit. Check for a burnt off wire at the contactor. For some reason you are not getting power to the outside unit. If you find a burnt off wire shut off all power to it then remake the connection at the point of the circuit break.
Posted on Jun 27, 2008
Tips for a great answer:
USE EXTREME CAUTION WHEN EXAMINING high voltage wiring.
Sep 08, 2013 | Goodman CLQ36AR49 Air Conditioner
Dec 06, 2012 | Goodman CLQ36AR49 Air Conditioner
Jun 10, 2012 | Goodman Heating & Cooling
Sep 20, 2011 | Goodman CLJ60AR61 Air Conditioner
Sep 11, 2010 | Goodman CKL60AR60 Air Conditioner
Aug 06, 2010 | Goodman CKL36AR36 Air Conditioner
Jul 17, 2010 | Goodman CKL42AR42 Air Conditioner
Apr 11, 2010 | Goodman CLJ36AR42 Air Conditioner
Jul 17, 2009 | Goodman CLQ36AR49 Air Conditioner
Jul 01, 2008 | Goodman Heating & Cooling
51 people viewed this question
Usually answered in minutes!