Question about Electrolux Heating & Cooling
Posted by Anonymous on
I'm not sure if all electrolux share the same error code table but most manufacturers have a common error report table for all of their own models. If that is the case, F2 is a indoor pipe sensor thermistor short/open fault. These are cheap and easily replaced.
If you have a multimeter, you can test the resistance of the pipe thermistor by disconnecting from the controller board and testing across the connector terminals of the thermistor wires. Resistance values are in the table attached.
You may have to get the service manual to be certain.
Posted on Oct 02, 2017
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 27, 2017 | Heating & Cooling
May 23, 2016 | Electrolux Heating & Cooling
Aug 22, 2013 | Heating & Cooling
Jun 15, 2013 | Heating & Cooling
Jul 25, 2012 | Heating & Cooling
Jun 04, 2012 | Heating & Cooling
Jul 16, 2011 | Heating & Cooling
Apr 30, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
169 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: