Question about Hardware & Accessories
I have hooked up the line 1 and line two with power supply but when I turn the timer on no slots have power I'm using n/o 1 and n/o2
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
T104 series intermatic timers are 208/230/277 volt clocks, not 120. I believe you have the wrong model and need a T101 series instead.
Posted on Jun 13, 2009
SOURCE: T101 R Clock will not turn
The "Line" is the power source. The "load" is the device that is being powered.
typically the green wire is the ground wire. I strongly urge you to verify your assumption that is is the common wire. If the green is indeed the ground, and it gets hooked up to common, you will be energizing the cabinet of the unit and posing a serious shock hazzard.
Your curcuit will be as follows.
The power source "Line" will have wires going to the timer. (hooked to the "line" terminals on the timer.)the timer then is supplying the power to the pool pump, and we will reffer to it as the "line".
The two black wires from the pump would be hooked up to the "load" side of the timer.
Typically they would be labled line 1 and line 2 or "L1" and "L2"
If yours are not labled so, describe exactly what terminals you have in detail in both the pump and the timer.
Posted on Oct 03, 2009
Testimonial: "Good Advice."
reading the specs i should say its a timer for only one zone. you can use it for one zone switching or for the pump. sorry.
Posted on Feb 14, 2010
WH40 is 240Volt timer.
WH40 will not work with 120V circuit.
See WH40 wiring illustration at following link:
There are two hot wires in 240V circuit because every circuit requires two wires to complete the circuit.
Hot wires from breaker connect to terminal 1 and 3.
Notice that small white wires are also connected to terminals 1 and 3.
Small white wires power clock motor located on back of mechanism, so this says power from breaker box must arrive on terminals 1 and 3. This insures that clock motor runs continuously.
If clock motor only runs when manual override switch is clicked ON, then your Hot and Load wires are reversed.
Bare ground wire connects to green ground screw.
Wires going to Load (water heater) connect to terminals 2 and 4.
FYI: Terminal A is not used unless circuit also has a Neutral wire,
See basic water heater circuit Diagram #2:
Terminal A is also used if you want to convert WH40 to 120V timer by replacing 240V clock with 120V clock.
How to convert Intermatic 240V timer to 120V timer
Posted on Dec 25, 2010
I don't have answer for defective timer. Buy another timer if everything below checks out:
59018 7-day timer has limited 1 year warranty, and appears to be made by Tork
Timer is for 120Volt single-pole only.
Rated for 1000 watt tungsten, 8A ballast, 1/4 HP
Push reset button with toothpick > not necessary to press-and-hold other button to accomplish reset.
After reset, 12:00 am Monday should display.
Programs are deleted. Reprogram timer.
To check, change and delete specific programming, press PROG key until selected program displays, and then set new programming >>> or press-and-hold MODE button and press PROG button again to delete selected program.
Timer has non-replaceable 30-day carryover battery and does not lose programming after power outage, and will retain programs until battery is depleted.
Hot to timer black.
Neutral to timer white.
Load to timer red.
Ground to timer green.
Lights will blink if timer red and timer white are connected to load together.
Timer will not function if timer black and red wires are reversed. Display will not show.
Posted on Aug 08, 2011
Tips for a great answer:
Jun 17, 2015 | Water Heaters
Aug 08, 2013 | Hardware & Accessories
Jun 18, 2011 | Intermatic INC ET104C 24 HOUR ELECTRONIC...
May 30, 2011 | Intermatic HEATER DELAY SHUT OFF SWITCH...
Feb 21, 2011 | Electric Intermatic Wh 21 Water Heater...
Dec 03, 2010 | Intermatic ET70115C Electronic Energy...
Oct 24, 2010 | Intermatic EH40 - Electronic Water Heater...
Aug 09, 2010 | Intermatic EH40 - Electronic Water Heater...
Oct 03, 2009 | Intermatic & Indoor/Outdoor Rain Tight...
138 people viewed this question
Usually answered in minutes!