Question about Hayward Gas Swimming Pool Heater 100k Btu Natural Gas
Posted by Anonymous on
Check gas pressure if too low it will overheat and shut off or run out of gas
Posted on Mar 19, 2016
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Low Flow errors are not necessarily real. They can be caused by improper adjustment or a defect of the pressure switch. Locate the pressure switch. Verify that the "switch" makes contact. Adjust the dial, reducing the distance the switch has to travel to engage. This will effectively lower the operating pressure required to operate. Keep adjusting until the unit stays on.
Posted on Apr 23, 2010
CE= Communication Error between Control Module
and Display Interface Assembly
1. Disconnect and then reconnect power to heater.
2. Check for faulty wiring or connection.
Inspect Display Interface Wiring. Ensure Display Interface Plug is securely attached to Control Module. .
3. Control Module and/or Display Interface Assembly
are defective.Replace Control Module and/or Display Interface Assembly.
Here is a linkt oH aywardmanuals:
Posted on Jul 05, 2010
Tips for a great answer:
Jul 06, 2014 | Hayward Pool & Spa
on Feb 06, 2011 | Cannon i70 Printer
Dec 01, 2013 | Frigidaire Electric Dryer
Nov 10, 2017 | Rheem RTG-66DVN Direct Vent Natural Gas
Aug 26, 2011 | Sta Rite Sr200lp Max E Therm Pool & Spa...
Aug 11, 2011 | Water Heaters
Jul 01, 2010 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Jun 05, 2009 | Kenmore 62602 Electric Dryer
Apr 25, 2009 | Kenmore 67082 Electric Dryer
Nov 26, 2008 | Frigidaire Affinity 5.8 Cu. Ft. Gas Dryer
Jul 12, 2010 | Hayward Gas Swimming Pool Heater 100k Btu...
24 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: