Question about AmcorAire UCHW-H12AF2 Split System Air Conditioner
The unit I bought was set up just a week ago and after my a/c guy fixed all the error messages that were coming up the unit still doesn't work properly.
The A/C will seem to be operating normally until anywhere between 4-6 hours later the unit while still sensing that it needs to cool the room only blows air at the same temp. as the room.
This is easily fixed by turning the unit on and then off again but this certainly won't work for me as I'm using the unit to cool a server room and as such is left unattended for long periods of time...
If the unit was set up a week ago the technician should warranty his work and come back and take care of the problem for you, not knowing what was set up and how, it's hard to say if it's a problem with the unit or the control (t'stat or programming if it's a programmable t'stat).
Posted on Mar 17, 2009
If this unit was new one and setting was done accurately,It sem that the ac is tripping off due to several factors in case of tripping off the compressor there is a hi pressure that building up on hi side that could not expand normally on expansion valve,there's clogging of some impurities or substance such as air in the system,this will develop a high current to your compressor exceeding to the rated current of unit,resulting to trip off the ac.You can check this on taking the operating current while the unit while is running using clamp ammeter the current will register and compared this to rated current that specified in the compressor manual or the compressor casing it was tag there.Or check again the set up sequence at the remote control the variation of thermostat setting.
Posted on Mar 13, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 25, 2012 | Intertherm 56000 Btu Gas Furnace
Feb 14, 2012 | Cell Phones
Mar 26, 2010 | Nikon COOLPIX L18 Digital Camera
Oct 15, 2009 | Garmin Nuvi 265W GPS Receiver
Jul 29, 2008 | Samsung SGH-D900 Cellular Phone
Mar 26, 2008 | LG KU990 Viewty
Jan 30, 2008 | Canon PIXMA MP530 All-In-One InkJet...
Jan 18, 2008 | Office Equipment & Supplies
Jun 21, 2007 | Microsoft Xbox 360 Console
Jul 12, 2014 | AmcorAire UCHW-H12AF2 Split System Air...
125 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: