Question about Electrical Supplies
How do i set my generator up for 110 right now its putting out 300 volts
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Your gas pressure is too low and you may not have a large enough supply pipe. You need at least 10 inches of water column with the engine running to operate an LP vapor fueled engine. Because the engine is starving for fuel, its governor opens the throttle to WOT (so it goes to high revs) but there isn't any fuel to make horsepower with so the output voltage falls and the undervoltage alarm trips.
Posted on Dec 03, 2008
Your RPM's are too high. There is no voltage regulator in coleman generators (generator is actually made by generac) and is 100% dependent on engine speed. There is a screw under the tank when your looking in from the recoil side. It controls the governor arm. Screw it in and it incresses the rpm, out decrease. Plug something in that draws a decent load while setting the rpms since you want it to put out 120 and 240 underload. Your idle voltage does not matter.
Posted on Apr 02, 2009
OC stands for Over Crank. How long does it take before the genset starts?
Posted on May 07, 2009
you know , i have helped several people on thire cars , i want a fix and you want money...not faiir at all....i thought this sight was a helpful sight...i see diferently now....thanks
Posted on Sep 03, 2009
Tips for a great answer:
Sep 20, 2016 | Kohler Electrical Supplies
Feb 12, 2013 | Kohler 12 kW Emergency Power System -...
Sep 10, 2011 | Coleman Powermate Powermate 5000W...
Sep 05, 2011 | Garden
Jul 14, 2011 | Makita G6100R 5800 Watt Generator
Feb 04, 2010 | Kohler 12 kW Emergency Power System -...
Nov 11, 2009 | Kohler 12 kW Emergency Power System -...
Jul 01, 2009 | Coleman Powermate Proforce 6,000 Watt 12...
71 people viewed this question
Usually answered in minutes!