Question about True T-49 Side by Side Refrigerator Commercial
If its getting warmer or more humid where you are this is probably a
sign of needing to clean your outer coils. Remove the panel covering
the compressor and check the condition of the coils. Clean with a nylon
brush or wire brush. Or blow out with compressed air.
If the outer coils look OK see if they feel warm up and down the sides. If they don't you may have a defrost problem. If they are warm recheck them in 30 minutes if still warm or warmer and no one has opened the door check the lite inside, and the fan inside (it will only run with door closed). Hit the switch and see if lite goes out and make sure the switch is being activated with the door closed. And check the door seals any vinyl cracked on them they need replacing but can be warped sometimes letting in warm air (usually a sign of frost inside the door or water leaking out but not always).
It could be low on refrigerant or an inefficient compressor but not likely as much as these other items are.
The last thing is the thermometer could be reading wrong or out of calibration. Is it Electronic? Yes - Then its most likely one of the other problem before. If its mechanical (bi-metal) get another thermometer you trust or a new one and check it before you trust it. 2 of them telling you its 5'f then Id believe it other wise one or both of them are wrong.
Posted on Mar 12, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 20, 2010 | True GDM-26 Refrigerator
Oct 03, 2010 | True 49 cu. ft. / 1388 liter Commercial...
Apr 23, 2010 | True 72 cu. ft. / 2039 liter Commercial...
Sep 21, 2009 | Arctic Air 22 cu. ft. Commercial Freezer...
Jul 12, 2009 | True 49 cu. ft. / 1388 liter Commercial...
Jul 11, 2009 | True 49 cu. ft. / 1388 liter Commercial...
Jun 25, 2009 | GE Refrigerators
May 17, 2009 | True 49 cu. ft. / 1388 liter Commercial...
Apr 07, 2009 | True 49 cu. ft. / 1388 liter Commercial...
Oct 09, 2008 | Beverage-Air 23.1 cu. ft. / 654 liter...
162 people viewed this question
Usually answered in minutes!