Question about Panasonic DBS Battery Backup Unit (VB43130X) UPS System
I have a single cabinet Panasonic DBS576 phone system. I need to get a UPS to keep this unit up for at least 30 minutes or more. I need to know the power consumption fo this unit. Please help.
Tony166, according to the web, the Panasonic DBS 576 single cabinet phone system will run at a peak wattage of 360 or 3.3 amps. 3.3 amps x 120V = 396 VA.
Also, this is a very sensitive device and needs good clean power to eliminate frequency variations and line noise. You should put this system on an On Line or Double Conversion UPS. Not a Line Interactive or an Off Line unit! Those are the 3 UPS industry standard technologies. The Off Line technology is simply a battery in a box. It can break down a clean sinewave input and feed your connected load a stepwave signal. The Line Interactive unit will provide a sinewave while on battery power, but not during normal operation. Only a true On Line UPS will provide pure sinewave power 100% of the time!
I would suggest at least a 1kVA or 1.5kVA Liebert GXT2 product!
Contact www.ropeconsulting.com for a quote!
Posted on Mar 13, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 27, 2012 | Panasonic Lands Phones
Sep 24, 2011 | MGE Galaxy 3000 UPS System
Sep 20, 2011 | Opti DS1500B UPS System
Aug 12, 2011 | APC SMARTUPS RT 15KVA RM 230V...
Nov 01, 2010 | Panasonic KX-TG1033S Cordless Phone
Oct 21, 2010 | Panasonic KX-T7630 Corded Phone
Jul 08, 2010 | Powerware Series 9 9150 UPS System
Oct 16, 2009 | APC Smart-UPS 700VA UPS System
Jun 21, 2008 | Lands Phones
Dec 27, 2007 | NEC APC Smart-UPS 1400 (050-01803-000) UPS...
Oct 23, 2007 | Panasonic DBS Battery Backup Unit...
82 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: