Question about Plumbing
I have a water softener with an Autotrol 255 valve. Occasionally after a regeneration cycle I find approx. 1/2 cup of resin has been discharged through the waste line. I have no issues when the valve is in the service position. Any ideas regarding where to check for a failure?? Thank you.
If you made it this far, you’ve just figured out what’s wrong with your water softener. There are a couple of things that can cause this. No it doesn’t mean that you have to throw your entire water softener away into some landfill. It can be fixed instead, possibly even at no cost.
First thing you need to check is the springs on top of the valve (in my guess this was the cause of losing resin). Take the cover off the top of the valve. Look at top of the valve, there are several metal springs. One or more of these springs may have come disconnected from the flapper valve(s). The springs will hold the flapper valves shut when they are supposed to be shut. I believe either me or someone before me did not put the valve back together correctly.
Alternatively, the flapper valves could be deteriorated, letting water/resign out. Also check the plastic dip tube that goes down into the tank, make sure nothing is broken there.
Posted on Mar 22, 2010
This is a problem you have some broken parts inside the tank you need to get this fixed. you are loosing your resin that is what sofens your water.
Posted on Jun 23, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 18, 2014 | Morton Salt Inc 15010000 Water Softener...
Aug 01, 2014 | Water Dispensing & Filtration
May 14, 2014 | Autotrol 263/740 Performa Logix Control...
Feb 05, 2014 | Reliance Water Dispensing & Filtration
Sep 03, 2013 | Pentair Water Dispensing & Filtration
Apr 13, 2017 | Dishwashers
Mar 09, 2011 | General Electric GE SmartWater Household...
Feb 26, 2011 | Culligan Compatible S7011C RS23SED5...
Jan 14, 2011 | NRS Fleck 5600 - 64,000 Grain Timer Water...
Apr 21, 2018 | Plumbing
444 people viewed this question
Usually answered in minutes!