Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: carrier heat pump
fuse is usually a small resetable breaker on the side of the transformer, or a traditional screwin fuse with a plastic cap on one end that is a specialty fuse and is available at most motor shops or elec supply houses. or its a auto type plug in fuse on the circuit board usually 5 amps or three amps. first turn the fan switch on the stat from auto to on. does fan run? if it does you have high and low voltage and your wired wrong. if it is in the stat you are usually looking at red connects to red . yellow to yellow, green to green , orange to orange, white usually to white, that leaves a common power wire to operate the stat, usually connected to the common term on the new stat . this can be any color and is necessary for the new stat to think and work, if it has batteries it will have a display but it needs a red and a common to think and work. this wire can be any color and if your old stat had no common which a lot didnt then youll have to add one. carrier also has a emergency heat strip wire sometimes labeled x2 etc. you can usually jump white over to x2 to perform function if needed. good luck.
Posted on Oct 25, 2008
Hi!!! Does your ac unit work fine?If not check your low voltage problem..You have a low voltage problem check the wire going out to your condensor make sure that they are not touching..Good luck..Check low voltage wires..short in progress..
Posted on Jan 04, 2009
SOURCE: My outdoor heat will not
you need to go oside and look for a red reset button on the unit. you tripped the high ressure switch when you let your filter get that dirty. go check on this and when your done if it still is not working then ask me more.
Posted on Jan 25, 2009
Tips for a great answer:
Jan 27, 2013 | Carrier Heating & Cooling
Dec 11, 2010 | Honeywell Electronic Programmable...
Oct 16, 2010 | Carrier Heating & Cooling
Jan 12, 2010 | Carrier 38CKC042 Air Conditioner
Nov 05, 2009 | Carrier Heating & Cooling
Jan 25, 2009 | Carrier Heating & Cooling
Jan 18, 2009 | Heating & Cooling
Jan 05, 2009 | Honeywell Programmable Thermostat Heater
Dec 20, 2008 | Carrier Heating & Cooling
Oct 27, 2008 | Carrier Heating & Cooling
19 people viewed this question
Usually answered in minutes!