Question about Goodman Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Typically if you have a yellow wire in the "y" terminal blue is used as common or "c". As far as your jumper from rc to rh, that will depend upon what type of heat you have. If all of your heat and cooling come from your packaged unit outside, yes you will need the jumper. If this does not work maybe you have a bad breaker or transfomer.
Posted on Oct 14, 2007
SOURCE: Honeywell Thermostat RTH 7500
Assumed all the wiring are correct,
to change from manual switching from heat to cool, press [system] button ( left ) to go into system setting.
then press and hold the [fan] middle button untill option display 120
use up down button to select option 300 ( Manual/Autochangeover) ,
select 0 for manual, 1 for automatic. ( read caution in page 22 of installation manual )
Posted on Oct 14, 2008
Hook up o to o/b, then in the installation programming set the change over valve to energize in cool. Then hook up w to aux. Good luck.
Posted on Jan 21, 2009
SOURCE: Need help with wiring thermostat
first do you have a heat pump unit or standard a/c? standard a/c connections at the thermostat go like this red wire to rh-rc which is the 24v power and you don't have to remove the jumper.white goes to w which is the heating wire yellow goes to y which is the cooling wire green goes to g which is the fan wire and blue goes to c which is the common wire. so if your stat has rc- rh ywgc you should be set if the wires on the furnace correspond with the same alpha designation.orange may be used if u have a heat pump unit otherwise it may just be a spare you cap off and leave behind the subplate.
Posted on May 31, 2009
Tips for a great answer:
Aug 25, 2013 | Honeywell RTH8580WF1007 7Day Touch...
Nov 12, 2011 | Honeywell Programmable Thermostat Heater
Oct 16, 2009 | Honeywell Electronic Programmable...
Aug 12, 2009 | Honeywell Electronic Programmable...
Jul 03, 2008 | Honeywell Heating & Cooling
Jun 02, 2008 | Honeywell Programmable Thermostat Heater
May 26, 2008 | Honeywell Power Humidifier: Furnace...
Feb 03, 2008 | Honeywell Programmable Thermostat Heater
282 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: