Question about Heating & Cooling
Fan running outside, no compressor startup, no cold or moist copper line, inside unit runs but no cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Inside fan running outside not
There is an electrical box on the wall near the outdoor unit. open it and be sure that the circuit breaker is in the on position. Same in your electrical panel, be sure that the circuit breaker is turned on.
Posted on Aug 16, 2009
are you speaking of the outside fan or inside? compressor should be a little warm but not boiling hot. the unit could be low on freon. if low it will run a while but the compressor will overheat and shut off leaving the fan running by itself ouside. if nothing outside is running check power. if you have power check the contacted outside to make sure it's pulled in. contacters are bad about going out on goodman untis. Also ants can get under contacts.
Posted on Jun 18, 2009
open the service panel to check for control voltage of 24volts when tstat calling, The contactor should be pulled in, if contactor is down,and contacts appear to be clean, and the unit is still not running, it is a bad compressor. to test this unplug the black wire from the compressoror at contactor,w/ power off! Turn on power if fan works normally it's a bad compressor. However if you see a swollen split cap(5 wires to a soup can looking w/ the terminal C,F,and Comp), switch it first and start at square one.
You also need to consider the high pressure switch if its cycling on off on off.
Posted on Mar 12, 2009
It sounds like you have a unit called a heat pump. When a heat pump unit is in cooling mode the outside unit blows hot air and the inside unit blows cold air. If the outside unit is blowing cold then the indoor unit is most likely blowing room temperature or warm air. It sounds like the thermostat could be controlling incorrectly or you could have a failed reversing valve which is the device that switches the unit from heating to cooling mode.
Posted on Jun 02, 2009
Tips for a great answer:
Jun 06, 2016 | Amana Heating & Cooling
Jun 18, 2014 | Goodman Heating & Cooling
Apr 10, 2017 | Heating & Cooling
Jun 19, 2010 | Weather King 10AJA4201AH Air Conditioner
May 18, 2010 | Carrier 38CKC036 Air Conditioner
Jan 23, 2010 | LG Heating & Cooling
Aug 15, 2009 | Heating & Cooling
Jul 26, 2009 | Heating & Cooling
Jun 26, 2009 | Heating & Cooling
Jun 02, 2008 | Heating & Cooling
386 people viewed this question
Usually answered in minutes!