Question about Heating & Cooling
I had a furnace guy here twice. Each time he replaced parts, each time the furnace stopped working shortly after he left. The blower motor starts, but the furnace won't fire. A friend tried calling Bryant, but they wouldn't say anything until they had the model number. Ihave searched hi and low on the unit, and no number. Suggestions? Parts replaced: Inducer motor, inducer control board, main control board, pilot and flame sensor.
Try checking the pressure sensing switch,it has a tube that should run somewhere close to the inducer fan.sometimes this hose fills with liquids,and makes the units act funny.I don't know if you have a condensing unit or what.the furnace wont try to light if it cant tell the inducer motor is running.any induced draft unit will work this way.you can also do a temp. bypass of the pressure switch to make sure the contacts on it are closing just be sure your inducer fan is running,and you cant leave it like that its just a test.that is a safety feature you really need.
Posted on Mar 19, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 08, 2016 | Heating & Cooling
Dec 29, 2012 | Bryant Single-Packaged AC & Gas Furnance...
Dec 23, 2012 | Heating & Cooling
Sep 19, 2011 | Heating & Cooling
Feb 19, 2011 | Heating & Cooling
Feb 06, 2011 | Heating & Cooling
Jan 31, 2011 | Heating & Cooling
May 11, 2009 | Heating & Cooling
Jan 24, 2009 | General Filters 1042-LH Humidifier
Feb 23, 2017 | Heating & Cooling
531 people viewed this question
Usually answered in minutes!