I had a furnace guy here twice. Each time he replaced parts, each time the furnace stopped working shortly after he left. The blower motor starts, but the furnace won't fire. A friend tried calling Bryant, but they wouldn't say anything until they had the model number. Ihave searched hi and low on the unit, and no number. Suggestions? Parts replaced: Inducer motor, inducer control board, main control board, pilot and flame sensor.
Try checking the pressure sensing switch,it has a tube that should run somewhere close to the inducer fan.sometimes this hose fills with liquids,and makes the units act funny.I don't know if you have a condensing unit or what.the furnace wont try to light if it cant tell the inducer motor is running.any induced draft unit will work this way.you can also do a temp. bypass of the pressure switch to make sure the contacts on it are closing just be sure your inducer fan is running,and you cant leave it like that its just a test.that is a safety feature you really need.
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need. goodluck!
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
A 13 code means the furnace cycled on limit more than three times consecutively and is in a lockout for 3 hours. A 14 is ignition lockout. An ignitor does not intermittently quit working. I'm the service mgr at our shop, and I know that particular furnace model has a service bulletin out on bad secondary heat exchangers. If your lucky the filter is dirty, or the furnace condensate trap or drain is clogged. Most likely the secondary heat exchanger is plugged up and isn't allowing the pressure switch to make. Or the furnace is overheating due to it not being able to properly vent hot gas. Which would explain the high limit lockouts. Call an authorized carrier dealer so you can take advantage of the free heat exchangers and the $300 labor credit. You can also call an authorized Bryant dealer to perform the work for you. Only an authorized dealer can rectify this problem because the Bryant corp requires testing and paperwork in order to get your free parts and labor credit. Good luck.
Hello my name is Heath it will be my pleasure to assist you. First thing to do is go to the furnace and look in the small peep hole in the lower blower door and see if there is an led light that is flashing a certain number of blinks record the number and look for a diagnostic chart on the inside of the blower door or the upper side panel of the furnace if there is no flash code present you can try resetting the power to the furnace and see if the furnace will fire up.
Hello, Make sure the flame sensor is clean near the burners, The flame sensor is a metal rod that is on the opposite side of the ignitor. To clean the flame sensor you will need some steel wool, turn off power to the furnace and remove the flame sensor and clean it with the steel wool. After cleaning reinstall it and turn power back on to furnace.
these codes are on the inside panel of the front cover of the furnace. lift off and look inside.there should be a code explain chart on the panel by the light. this panel will need to be replace correctly for the furnace to work as there is a door switch.
theholts220 - Sounds like they needed to install a bit larger transformer . You can also buy a A 50 Sensing relay that attaches to the wires for your motor and when you turn on the furnace it will allow the power to go to the humidistat. Very strange though they do not use a lot of power. Check and make sure the wires are not pinched or touching metal somewhere.
TLuzzo - The humidistat seems to be working when you turn it down. The wires for the solenoid should be hooked up to your furnace circuit board. The instruction manual will tell you where. If you dont have a spot on your circut board the A 50 sensing reley is they way to go. They are inexpensive