Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Fedders Air conditioner
e5 is comp overload code . if you have infared remote for indoor units point at anyone while pushing all 3 buttons at the same time- 'mode' 'temp up' temp down' this will bring up OO where temp set point is normally displayed. scroll up or down with temp up or down buttons (1st digit only) untill you here the beeping sound change tone, this is the 1st part of the fault code. press mode once to change to 2nd digit, scroll again with up and down listening for change of beep- 2nd part of code ie "E5". press mode again will bring up afunny looking T-test mode. press mode again to exit. THATS VERY ACCURATE SOLUTION.SAVE IT FOR FUTURE.WISH U SUCCESS .REPLY FOR FURTHER ASSISTANCE IF REQUIRED.BYE
Posted on Jun 07, 2008
signal of indoor
1、Check whether two sets of plugs on the outlet end of
the motor have loosed from the socket of the
electric control board, insert it firmly when loosing.
2、Check whether the indoor motor has damaged, the
motor should be replaced when it is damaged
3、 Check whether the controllable silicon and other
components on the electric control board have
damaged, replace the controllable silicon or electric
control board when they are damaged.
Posted on Jun 26, 2010
Tips for a great answer:
Aug 14, 2014 | Heating & Cooling
Dec 16, 2010 | Heating & Cooling
Sep 06, 2010 | Heating & Cooling
Jun 12, 2010 | Heating & Cooling
May 27, 2010 | LG LSC183VMA Split System Air Conditioner
98 people viewed this question
Usually answered in minutes!