Question about Heating & Cooling
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: air conditioner
I managed to find the people who supplied the unit, it was still under warranty, and they said it was the thermistors (temprature probes, they replaced both of them) It is now working perfectly!
Posted on Sep 24, 2008
Do you mean thermostat, the wireless controller for air conditioner? we are exporter of this line from China. Should you be interested in our products. Please feel free contact me at email@example.com or add my MSN firstname.lastname@example.org. Our website is www.yseagroup.com
Posted on Oct 20, 2008
SOURCE: Air Conditioner Error code?
E5 is a coil sensor problem,this can be caused if you have had dirty filters, damaged the coil sensor while cleaning it or a common problem on any air conditioners, ring the boys at ager on 33412663 as they are very helpfull and will rectify the problem staright away for you
Posted on May 06, 2009
The unit is overheating and tripping the internal overload of the compressor. Clean outdoor coils.....check outdoor fan to see if it turns or is siezed......possible bad Start/Run Capacitor which is a very common failure on condensing units......possible bad fan motor need replaced! Unit compressor can be cooled with a water hose to get it to reset the internal biometalic high limit switch that is located in the hermetically sealed compressor!
Posted on Aug 22, 2010
Tips for a great answer:
May 03, 2016 | Heating & Cooling
Apr 03, 2016 | Heating & Cooling
Jan 23, 2016 | Heating & Cooling
Jan 01, 2016 | DeLonghi Heating & Cooling
Nov 17, 2015 | Midea Westpointe, 12,000 BTU, Thru The...
Jul 28, 2014 | Samsung AQV12VBE Vivace Wall Heat Pump Air...
Aug 14, 2011 | Heating & Cooling
Aug 01, 2011 | Mitsubishi Mr. Slim MXZ30TN Air...
May 23, 2018 | Heating & Cooling
20 people viewed this question
Usually answered in minutes!