Question about Coleman Heating & Cooling
If you are calling for heat and the thermostat is set for 2 degrees higher than room temp, the heat pump and strips come on.
When the room temp and stat temp are less than 2 degrees the strips turn off.
That is, unless the installer wired the t-stat for the strips to stay on.
If they are coming on in the air/cool mode then you have a bad heat relay or a t-stat wire shorted.
Posted on Mar 11, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Is this a central heat? From the size i assume it is.
You say air conditioning on part of your question then use heat pump on another part. So it is important for us both be on the same page.
With all due respect some people think they have a heat pump and it is just AC and electric heat also but is not a heat pump.
. If you have the outdoor AC unit running with your thermostat set for heat and the air coming off the out door unit is cold, or you see it "steam up outdoors" off the out door unit at times (we call this mode defrost).
If you actually have a Heat pump system some times it is wired to have the strips come on at the same time the heat pump comes on especially if you experience a lot of weather below 40' occasionally and have an emergency heat setting on your thermostat you most likely have a heat pump.
If you have a heat pump for sure now the heaters can come on with the outdoor section if
1 they are wired to do so or
2 the thermostat has 2 stage heating and the second stage is telling the elements to come on, or
3 the outdoor thermostat (if so equipped) is telling the elements to come on.
Any 1 or combination of these 3 items can cause the elements to come on wit the out door unit.
Posted on Mar 12, 2009
Tips for a great answer:
Jul 28, 2015 | Heating & Cooling
Jan 01, 2015 | Goodman Manufacturing Goodman GPH1348M41 4...
"PLACE A JUMPER (PIECE OF WIRE) BETWEEN Y AND W IF YOU ARE USING A HEAT PUMP WITHOUT AUXILIARY/BACKUP HEAT." if this dosnt work check the fuse in the air handler you may have blown it if you did not turn the unit off before installing.
Mar 25, 2014 | Goodman Heating & Cooling
Aug 22, 2011 | Goodman CKL36AR36 Air Conditioner
Mar 11, 2011 | Heating & Cooling
Nov 06, 2010 | Coleman Mach III Air Conditioner
Apr 23, 2010 | Coleman Heating & Cooling
Oct 12, 2009 | Heating & Cooling
Mar 12, 2009 | Coleman Heating & Cooling
Jan 18, 2009 | Goodman CKL49AR49 Air Conditioner
Dec 10, 2017 | Coleman Heating & Cooling
241 people viewed this question
Usually answered in minutes!