Question about Honeywell HE220A1019 Whole House Humidifier Humidifier
Is it normal or abnormal? Any solution?
I has the same problem with my HE360 unit. The unit was in fact miswired. The head unit red wires were connected directly to the blue solenoid wires, and activated the solenoid without any signal from the humidistat. As soon as the unit is plugged inn, the water starts running without any signal to the unit. If your unit is miswired, the soleniod blue wires need to be cut and connected to the red crimp connectors.
Posted on Oct 18, 2011
I had the same problem with my Honeywell HE 265. I ordered part number 32001639-002 from simplyplumbing.com and fixed it today. The solenoid is the same for the HE 220. You'll need a torx screwdriver and a 5/8" wrench. Doesn't matter how you re-attach the electricals, they're DC.
Posted on Apr 26, 2009
No turn the furnace switch off (the light switch near furnace, if water continues replace solenoid valve. Afterward you adjust to a slow trickle when calling for humidity, anymore is wasted water.
Posted on Mar 12, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 28, 2016 | Honeywell he225h8908 bypass humidifier,12...
Unless you are using a current sensing relay or sail switch, you need to get the humidifier power from the blower motor supply so it only operates when the blower is on.
Since you can manually control the humidifier, there is not a fault with the solonoid.
Oct 19, 2007 | Honeywell HE360A1027 Whole House...
Nov 10, 2013 | Honeywell HE360A1027 Whole House...
Apr 14, 2011 | Vicks Warm Mist V745A 1 Gallon Humidifier
Mar 25, 2011 | Vicks Warm Steam Vaporizer 1.5 Gallon...
Feb 23, 2011 | Honeywell HE360A1027 Whole House...
Feb 22, 2011 | Vicks Warm Steam Vaporizer 1.5 Gallon...
Feb 12, 2011 | Vicks Cool Mist V3500 Humidifier
Jan 28, 2011 | Honeywell HE220A1019 Whole House...
Jan 24, 2011 | Honeywell HE365 Humidifier
1,491 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: