Question about Carrier XHB123D X/Y Series Heat/Cool Air Conditioner
When the furnace is turned on the signal from the printed circuit board that operates the pilot has a hard time getting to the pilot causing the pilot to be intermittent.
It does have a pilot? Is it spark ignited? I suppose this is the clicking your talking about. try blowing the pilot area out with compressed air and blow all around the base of the pilot. Then retry it. see if the flame looks stronger after this too. If its still acting up you may have a ground that's not very good. try removing the burners and manifold and cleaning them and vacuum the heat exchanger out while apart. then while putting it back together look for anyplace that may have had a ground wire attached and is now gone.replace this and see if it improves .
Posted on Mar 12, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 08, 2015 | Williams Heating & Cooling
on Dec 04, 2009 | Heating & Cooling
Sep 06, 2011 | Ruud UBHC Air Conditioner
Feb 03, 2011 | Goodman Heating & Cooling
Feb 01, 2011 | Heating & Cooling
Feb 09, 2010 | Dometic Rooftop RV Air Conditioner
Nov 27, 2009 | Honeywell CT87B ROUND HEATING&COOLING...
Nov 18, 2009 | Goodman GDS80904BNA Open Flame Heater
Feb 24, 2009 | Dayton (4LX41) Heater
49 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: