Question about Carrier XHB123D X/Y Series Heat/Cool Air Conditioner
When the furnace is turned on the signal from the printed circuit board that operates the pilot has a hard time getting to the pilot causing the pilot to be intermittent.
It does have a pilot? Is it spark ignited? I suppose this is the clicking your talking about. try blowing the pilot area out with compressed air and blow all around the base of the pilot. Then retry it. see if the flame looks stronger after this too. If its still acting up you may have a ground that's not very good. try removing the burners and manifold and cleaning them and vacuum the heat exchanger out while apart. then while putting it back together look for anyplace that may have had a ground wire attached and is now gone.replace this and see if it improves .
Posted on Mar 12, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 28, 2017 | Heating & Cooling
on Dec 04, 2009 | Heating & Cooling
Dec 08, 2015 | Williams Heating & Cooling
Sep 06, 2011 | Ruud UBHC Air Conditioner
Feb 03, 2011 | Goodman Heating & Cooling
Feb 09, 2010 | Dometic Rooftop RV Air Conditioner
Nov 27, 2009 | Honeywell CT87B ROUND HEATING&COOLING...
Nov 18, 2009 | Goodman GDS80904BNA Open Flame Heater
Feb 24, 2009 | Dayton (4LX41) Heater
53 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: