Question about Carrier XHB123D X/Y Series Heat/Cool Air Conditioner
Could be a loose blower wheel. It has slipped and touching the sides of the blower housing.
Turn off the power to the nit.
Remove the 2 bolts holding the blower in place.
Make yourself a wiring schematic.
Remove the wires.
Be careful not to touch the capacitor.
Remove the blower housing.
Clean the blower blades.
Spin the wheel to see where it is hitting.
Loosen the set screw on the motor shaft and adjust your blower wheel.
Posted on Mar 10, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jun 06, 2016 | Carrier Weathermaker 8000 Gas Furnace 125k...
Oct 20, 2014 | Carrier Weathermaker 8000 Gas Furnace 125k...
Sep 19, 2017 | Carrier Weathermaker 8000 Gas Furnace 125k...
Oct 30, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Apr 19, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 28, 2009 | Heating & Cooling
Jun 18, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
422 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: