Question about Carrier XHB123D X/Y Series Heat/Cool Air Conditioner
Could be a loose blower wheel. It has slipped and touching the sides of the blower housing.
Turn off the power to the nit.
Remove the 2 bolts holding the blower in place.
Make yourself a wiring schematic.
Remove the wires.
Be careful not to touch the capacitor.
Remove the blower housing.
Clean the blower blades.
Spin the wheel to see where it is hitting.
Loosen the set screw on the motor shaft and adjust your blower wheel.
Posted on Mar 10, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 20, 2014 | Carrier Weathermaker 8000 Gas Furnace 125k...
Nov 20, 2010 | Heating & Cooling
Oct 30, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 04, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 28, 2009 | Heating & Cooling
Nov 04, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Apr 20, 2009 | Carrier Heating & Cooling
388 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: