Question about Electric Circuit Breaker Kit for Furnace
Hello, You can try re-terminating the connector with a crimp on style connector. Just make sure the wire going to the element is in good shape. If the calrod heater element has shorted out it may burn the at the connection again. If not, you have fixed it! Good luck...gary
Posted on Mar 13, 2009
Tips for a great answer:
Jul 28, 2014 | Circuit Breakers & Wiring Panels
Jan 08, 2014 | Circuit Breakers & Wiring Panels
Oct 11, 2010 | Connecticut Electric Square D Packaged...
Jul 04, 2010 | Circuit Breakers & Wiring Panels
Apr 13, 2010 | Siemens 50 Amp Ground Fault Circuit...
Mar 15, 2010 | MotorGuide Circuit Breakers & Wiring...
Feb 08, 2010 | Circuit Breakers & Wiring Panels
Nov 26, 2009 | Gb Electrical 1 30 Amp Ground Fault...
Nov 02, 2009 | Circuit Breakers & Wiring Panels
101 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: