Question about Coleman Propane Forced Air Heater w/Electronic Ignition (50,000-80,000 BTU)
Remove the burner and gas valve from the furnace and use compressed air
to blow the area under the pilot area ans all around it. The dust and
stuff usually cause a condition called "Lazy Pilot" and the flame is
probably not going in the designed directions. While you have it out Id
replace the thermocouple with a new one reassemble and re-lite and
note the difference. The flame should be mostly Blue and no yellow (or
vary little at the top end of the flame only) Orange in the top area
indicates a good burning flame and the closer to the base the bluer it
While you have the burner out look inside and inspect the inner heat exchanger for cracks or rusted open holes there should be none. Turn on your fan while inspecting and see if you feel the steady blow of air from it inside the heat exchanger indicating a hole. Don't confuse the air that may come down the flue with the air from the blower though. A little breeze is expected from this.
This will take care of over 90% of the problems with the "Blow out" symptom.
If you still have problems you can try and "turn up the pilot". Usually a screw close to the pilot tubing is covering the adjustment screw. Put some soap bubbles around it so you can see if it leaks or not and turn the screw out for more flame (CCW) and in (CW) for less.
Hope this helps Please grade me accordingly and good luck.
Posted on Mar 11, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 03, 2015 | Coleman Propane Forced Air Heater...
Feb 16, 2015 | Coleman 7990-319p Evcon Gas Furnace...
Oct 07, 2014 | Coleman 7990-319p Evcon Gas Furnace...
Oct 15, 2013 | Heating & Cooling
Nov 12, 2009 | Heating & Cooling
Oct 08, 2009 | Heating & Cooling
Sep 16, 2009 | Coleman Propane Forced Air Heater...
Jan 21, 2009 | Coleman Propane Forced Air Heater...
Nov 10, 2008 | Heating & Cooling
May 15, 2014 | Coleman Propane Forced Air Heater...
498 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: