Question about Heating & Cooling
This can be caused by moisture in the system and when the moisture freezes on the capilliary tube you get a fluctuation, it the defrosts and passes through and again causes an up and down. Same would apply for excessive air in the system. You would have to do a long vacuum and possibly instal an inline filter drier.
Posted on Mar 10, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 01, 2012 | 2001 Chevrolet Silverado 1500
May 11, 2011 | Goodman Heating & Cooling
Dec 31, 2009 | Vintage Keeper Koolspace Wine Cellar
Jul 31, 2009 | 2000 Honda Civic
Jul 11, 2009 | 2006 GMC Sierra 1500 2WD
Jun 28, 2009 | 1995 Chevrolet C1500
Jun 13, 2009 | 2003 Chevrolet Silverado 1500
33 people viewed this question
Usually answered in minutes!