Question about Coleman Propane Forced Air Heater w/Electronic Ignition (50,000-80,000 BTU)
Check for continuity through all your switches. Check voltage where these switches hook up to your control ignition box.if you see voltage there the problem is either the wiring or one of your switches is open. If you read no voltage there check again from "C" to the same wires a readign then indicates a bad board. Then check "R" to there a reading here indicates a bad thermostat (which is probably not your trouble due to the code and your legend of the code 4)
Hope this is cleaR and helps Please grade am accordingly and good luck.
Posted on Mar 11, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 09, 2017 | Coleman Heating & Cooling
Jan 08, 2017 | Coleman Heating & Cooling
Jan 08, 2017 | Heating & Cooling
Jan 04, 2017 | Heating & Cooling
Jan 03, 2017 | Coleman Heating & Cooling
Jan 03, 2015 | Heating & Cooling
Nov 11, 2014 | Heating & Cooling
Nov 28, 2013 | Heating & Cooling
May 15, 2014 | Coleman Propane Forced Air Heater...
189 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: