Question about Maytag Dryers
I have a maytag performa when it run so long the breaker get hot and it kicks the breaker off, i have a 30amp breaker should it be a 40amp. It jus started doing this after 4 month. are could the breaker be bad.
Look on the unit for the electrical data plate. It should have the required amperage rating on it.
Have the actual amperage being pulled by the unit checked.
You may have improper voltage being supplied to the unit which causes excessive amperage.
The breaker could be weak. Meaning that it may be tripping at an amperage less than 30.
Your wire size may be too small for the circuit which would cause overheating of the circuit and tripping the breaker.
Do not change the breaker to a higher amperage unless the wire size attached to that circuit is rated for it.
A breakers job is to stop power should a overheating of circuit or a short circuit occurs. It protects the circuit from catching fire inside the walls and burning the place down.
Good Luck and I hope this helps.
Posted on Mar 08, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 12, 2011 | Maytag PYE2300AY Electric Dryer
May 21, 2010 | Maytag Bravos 7.0 Cu. Ft. Electric Dryer
Jan 02, 2010 | Maytag Dryers
Oct 26, 2009 | Frigidaire GLEQ2152ES Electric Dryer
Jan 26, 2009 | Maytag PYE2300AY Electric Dryer
Dec 29, 2008 | Maytag PYE2300AY Electric Dryer
114 people viewed this question
Usually answered in minutes!