Question about Intermatic T103 Indoor 120-Volt 40-amp Timer Switch-Double Pole/Single Thro
Wired the timer by the wiring diagram and timer isn't moving.
The wiring diagram for that timer is somewhat misleading. The 120 volt clock timer motor is connected internally to the "A" (neutral) terminal and the #3 terminal. The "A" (neutral) terminal is to the immediate left of the #1 terminal.
Here's how to do the wiring for your use, (assuming a 120 volt supply circuit and a 120 volt lighting or other load):
Connect the incoming power (line) black wire to terminal # 3. Connect the incoming (neutral) white wire to terminal "A".
Connect the outgoing (load) black wire to terminal # 4.
Connect the outgoing (neutral) white wire to terminal "A".
Posted on Mar 08, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 21, 2013 | Hardware & Accessories
May 14, 2013 | Hardware & Accessories
Jun 23, 2012 | Intermatic T104 24h 208-277v Mechanical...
Nov 29, 2011 | Home
Aug 20, 2011 | Intermatic & Indoor/Outdoor Rain Tight...
Jul 27, 2011 | Intermatic & Indoor/Outdoor Rain Tight...
Jun 01, 2011 | Intermatic & Indoor/Outdoor Rain Tight...
Mar 06, 2011 | Intermatic T8845PV - Sprinkler-Irrigation...
Dec 26, 2010 | Intermatic T104 24h 208-277v Mechanical...
Jul 14, 2009 | Intermatic & Indoor/Outdoor Rain Tight...
475 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: