Question about Honeywell HE260A1010 Whole House Humidifier Humidifier
A week ago I installed a Honeywell HE260 replacing an old Kemmore humidifier. It worked fine. I just went downstairs and noticed that the top of the humidifier housing was loose from the mounting. Upon further inspection I could see theat the top of the housing appeared to have deformed and warped from the heat. I followed the instruction and know that the I didn't mount the unit to low (actually it is a high as possible).
I plan on exchanging it for another unit but I am concerned it will just happen again. Any suggestions woul be helpful. Thank you
Humidifiers are made from a very durable heat resistant plastic. If it melted or warped you have a serious overheating problem. That plenum should not get over 140 to 155 degrees. If this furnace is running to hot it could stress and crack your heat exchanger. Install a good carbon monoxide detector in your home!!!! Check your filters. Check your airflow. Make sure all registers in the house are open. Is your blower speed set high enough? If this furnace is operating to hot it is definitely worth the investment to have a pro look at it before you replace the humidifier.
Is this overheating problem new? Or was this something thar happened years ago and may have since been solved But you are just now noticing the heat damege that was caused.
Posted on Mar 08, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 30, 2011 | Honeywell HE260A1010 Whole House...
Unless you are using a current sensing relay or sail switch, you need to get the humidifier power from the blower motor supply so it only operates when the blower is on.
Since you can manually control the humidifier, there is not a fault with the solonoid.
Oct 19, 2007 | Honeywell HE360A1027 Whole House...
Dec 19, 2010 | Honeywell HE220A1019 Whole House...
Jan 16, 2010 | Honeywell DWM-250 Humidifier
Dec 28, 2009 | Honeywell HE260A1010 Whole House...
Feb 01, 2009 | Honeywell HE360A1027 Whole House...
Dec 05, 2008 | Honeywell HE360A1027 Whole House...
Nov 30, 2008 | Honeywell HE260A1010 Whole House...
Nov 25, 2008 | Honeywell HE260A1010 Whole House...
377 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: