Question about Connecticut Electric & SWITCH UBIP130 "PUSHMATIC" SINGLE POLE CIRCUIT BREaker
You need to put in what we call a sub box. This should be done by a licensed electrician, but if you really want to do it yourself you will need a distribution box some wire and it has to be connected directly to your main lags from the meter box, this box will have a main breaker built into it and spaces for additional breakers, depending on your existing wiring the electrician might chose to wire the additional box directly to your meter base and not your existing box. Either way you really should seek local professional help on this project, just for your safety and to satisfy your home-owners insurance.
Have a great day..
Posted on Mar 24, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 19, 2012 | RTO Pushmatic 40Amp 2-pole circuit breaker
Jun 17, 2010 | Bulldog Pushmatic 31115 P115 15 Amp...
Apr 24, 2010 | Bulldog Pushmatic 31115 P115 15 Amp...
Apr 03, 2010 | RTO Pushmatic 100Amp 2-pole circuit...
Jan 25, 2010 | Bulldog Pushmatic 31115 P115 15 Amp...
Dec 23, 2009 | Bulldog Electrical Supplies
Oct 29, 2009 | Bulldog Pushmatic 31115 P115 15 Amp...
Aug 02, 2009 | Bulldog Pushmatic 31115 P115 15 Amp...
Feb 11, 2009 | Connecticut Electric & SWITCH UBIP130...
202 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: