Question about Spa Parts Plus GFCI, Circuit Breaker, 30 Amp
Load neutral connects to the neutral binding screw on the GFI, do NOT connect the load neutral to the neutral bar.
Posted on Mar 05, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 09, 2015 | Rheem 82V30-2 30 Gallon 240V Electric...
Apr 18, 2013 | Pool & Spa
Dec 23, 2012 | Electrical Supplies
Oct 02, 2012 | Electrical Supplies
Mar 05, 2011 | Cutler Hammer Gfi Breaker 2 Pole 20 Amp
Feb 05, 2011 | Fahrenheat Ceiling-Mount Industrial Heater...
Dec 28, 2010 | RELIANCE ELECTRIC WATER HEATER
Oct 21, 2010 | Intermatic T103 Indoor 120-Volt 40-amp...
Oct 13, 2010 | Intermatic T104 24h 208-277v Mechanical...
Jan 04, 2009 | Electrical Supplies
905 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: