Question about Spa Parts Plus GFCI, Circuit Breaker, 30 Amp
Load neutral connects to the neutral binding screw on the GFI, do NOT connect the load neutral to the neutral bar.
Posted on Mar 05, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 15, 2014 | GE 20 Amp 1 In Double Pole Circuit Breaker...
Dec 23, 2012 | Electrical Supplies
Oct 02, 2012 | Electrical Supplies
Feb 24, 2012 | Square D QO115GFI QO Circuit Breaker
May 08, 2011 | Bryant 50 Amp 2 Pole Br250 Type Br Ni...
Mar 05, 2011 | Cutler Hammer Gfi Breaker 2 Pole 20 Amp
Feb 18, 2011 | Cutler Hammer 100 Amp Main Breaker...
May 17, 2010 | Cutler Hammer Gfi Breaker 2 Pole 20 Amp
Apr 13, 2010 | Siemens 50 Amp Ground Fault Circuit...
Jan 04, 2009 | Electrical Supplies
903 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: