Question about Weather King 12AJA4801AH Air Conditioner
My furnace does not ignite, blower turns on but no flame
Tips for a great answer:
Oct 01, 2015 | Air Conditioners
Dec 02, 2010 | Air Conditioners
When there is a Call for heat, the control delays ignition until combustion air
Blower operation has been proved and pre-purge period
Has elapsed. It then opens the gas valve and generates a
Spark to ignite the burners. Trial for ignition lasts for 7 seconds.
At the same time, the control begins monitoring the
Flame sensor. If the flame current is too weak (less than 1
Micro amp) or if the burners do not ignite (within the 7 second
Ignition trial), the control will shut off spark and the combustion
Air blower and de-energize the gas valve. Flame
Current should be between 1 and 5 micro amps to keep the
Gas valve open.
The control will attempt to ignite the burners up to two more
Times. Each time the control restarts the ignition sequence,
It begins with a 45 second pre-purge. If flame is not sensed
After the third trial, the control locks out. Lockout means that
The control shuts off the gas valve, spark and combustion air
Blower for 60 minutes. At the end of 60 minutes the control
Completely resets and will attempt ignition up to three times.
The control can be manually reset before the end of 60 minutes
By momentarily turning off power to the unit.
here is a link to an operations manual
Nov 25, 2010 | Air Conditioners
Mar 03, 2010 | Ruud Matching Split Air Conditioner
Jan 16, 2010 | Weather King Air Conditioners
Jan 18, 2009 | Intertherm P3RA-048K Air Conditioner
Jan 16, 2009 | Air Conditioners
Jan 06, 2009 | Air Conditioners
May 21, 2008 | Air Conditioners
Jan 06, 2008 | Weather King 12AJA4801AH Air Conditioner
476 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: