Question about Honeywell CT87B ROUND HEATING&COOLING MECHANICAL THERMOSTAT - WHITE Heater
You should have a minimum of four thermostet wires. The red wire goes on the R terminal. White wire on the W terminal. Green wire on the G terminal. Place the yellow wire on the Y terminal. In most cases NO other terminals are used...... IF YOU DO NOT HAVE A YELLOW WIRE...... place the blue wire on the Y terminal. This should hopefully fix it. IF NOT....See if the thermostat has a RH and a RC terminal. If so I'll bet that you put the red wire on RC ternimal. this is for airconditioning ONLY. The RH terminal is for heating ONLY. Put a small jumper wire that will connect RH & RC. Then this should solve your problem.
Posted on Mar 08, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 08, 2017 | Honeywell Heating & Cooling
"PLACE A JUMPER (PIECE OF WIRE) BETWEEN Y AND W IF YOU ARE USING A HEAT PUMP WITHOUT AUXILIARY/BACKUP HEAT." if this dosnt work check the fuse in the air handler you may have blown it if you did not turn the unit off before installing.
Mar 25, 2014 | Goodman Heating & Cooling
Apr 11, 2013 | Honeywell Programmable Thermostat Heater
Feb 28, 2017 | Heating & Cooling
Oct 16, 2009 | Honeywell Electronic Programmable...
May 29, 2009 | Heating & Cooling
Nov 24, 2008 | Honeywell Electronic Programmable...
Oct 30, 2008 | Honeywell Heating & Cooling
Dec 01, 2013 | Honeywell CT87B ROUND HEATING&COOLING...
304 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: