Question about Fedders AEY08F2FCOM Wall/Window Air Conditioner
Your compressor ismounted or rubber feet. If one or more of these rubber spacers is gone or loose you need to come up with some more. If these are still n place its possible that the compressor (which is mounted inside the black oval or round case) may have a broken spring. In this case its compressor time Im assuming your fan is ok as you say its only when the cooling is on. Only 4 things move on the AC 1= inside fan 2= outside fan 3= fan motor and 4=compressor& compressor moptor which are in 1 case.
If you need to know more add on more information but I believe if youve gave me all you can thhin of its something to do with the compressor.
OH yes FYI if the outer case of the compressor is round you have a rotary compressor and they arenatorious for being loud and viberating even when new. If you decide its inside the compressor Id suggest replace the whole thing cause the compressor viberation causes tyhe copper lines to become hard and can crack eaisly. Hope this helps. PLEASE Grade me ACCORDINGLY and good luck.
Posted on Mar 03, 2009
Tips for a great answer:
Jul 27, 2015 | Sanyo Air Conditioners
Jun 04, 2011 | Air Conditioners
Apr 11, 2011 | Air Conditioners
Feb 15, 2011 | Samsung Air Conditioners
Jan 03, 2011 | Convair Air Conditioners
Dec 24, 2010 | Fujitsu 18C1 Air Conditioner
Jul 06, 2010 | LG Heat cool Window Air Conditioner
Feb 01, 2009 | LG LS-K1830CL Cool Mini Split Air...
Aug 03, 2008 | Air Conditioners
273 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: