Question about Ruud UBHC Air Conditioner
The Watt Restrictor in my Rheem 11kW Electric Furnace (RBHC-14J11SFA) is shutting off 2 out 3 heating elements, meaning the room I am trying to heat never reaches its setpoint.
Consequently, the furnace fan and a single heating element runs continuously, never reaching the setpoint.
Each morning, the room is around 56F, the setpoint is 65F. It takes 90min to reach 61F, and it does not get any warmer. Assume the outside temp is around 15-20F.
I used a current clamp to verify only one heating element is energized MOST of the time; however, the other two elements do turn on for short periods before turning of again.
Is there any way to safely disable/override the Watt Restrictor? I want to prove that the three heating elements can achieve the desired temperature rise.
Note: I have a Lux single-stage thermostat. Wiring of the thermostat matches the recommendation on the furnace's wiring diagram.
Unfamiliar with watt restrictors.
heat strips have 2 safety devices, a thermal overload, they get to hot they shut off, cause not enough air flow increase fan speed this device is auto reset. a fusible link a fail safe to thermal over load, no reset and sometimes replaceable. if this does not help would like to ask you a few questions. one of the buildings i take care of has 200 + reem/ ruuds all electric heat. if a part is defective replace, please do not by pass. safety frist.
Posted on Mar 07, 2009
Tips for a great answer:
Dec 03, 2014 | Ruud Air Conditioners
Mar 12, 2013 | Ruud Rheem Weather King Furnace Air...
Mar 08, 2013 | Ruud Air Conditioners
Sep 29, 2012 | Ruud Air Conditioners
Apr 03, 2011 | Air Conditioners
Feb 08, 2011 | Ruud Air Conditioners
Dec 22, 2008 | Ruud UBHC Air Conditioner
Dec 11, 2007 | Ruud UBHC Air Conditioner
1,201 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: