Question about Goodman GMS90703BXA Heater
The heater functions properly when I wiggle the small black/white/red wires going into the inducer motor . I'm assuming they send the board a signal to open the gas valve and fire up the unit .
The center frame and bearing plates are not tightened up and it's trying to shake itself apart , so I'm guessing those wires are loose inside also .
If , when I remove and inspect the motor , it can't be repaired , where's the best place to get a replacement at a decent price ?
Sounds like you may have a bad connecton at the end, which end? if you follow the wires out of the motor they sometimes go to a MOLEX whitish plug. The wires treminate in this plug with PINS sometimes these PINS dont seat or come loose in the plug. Pull the plug apart and check the wires comming in from both directions. If they wont push or pull out of the plug either way they are seated ok. Check for a bent PIN while have it apart. If its worse and this dosnt fix it or its the end going to the motor consult www.carrier.com for a dealer near you. DO NOT USE A GENERIC MOTOR on your furncae as I believe it is a 2 speed and most generic motors ar only 1 speed. SOme of these gaspack motors have a centrifical switch and if this is your problem again consult with a carrier dealer. The price of the motor is secondary to safety and longvity of your comfort investment. If I knew where you lived I could make a better recomendation.
A viberation could mean a HORNET nest (using mud for their nest) could have been in place and reciently came loose and fell into the fan on the motor. carefully remove the assembly and inspect it for bent fan or shaft or maybe plastic and broken or metal rusted out parts.
If you need more information I need to know a few more things. If this helps you r not please grade accordingly and help me improve. THANKS AND GOOD LUCK.
Posted on Mar 02, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 06, 2014 | Goodman GDS80904BNA Open Flame Heater
Aug 06, 2017 | Carrier Heating & Cooling
Jan 22, 2012 | Goodman GMS90703BXA Heater
Oct 04, 2009 | Dayton Electric Heater
Aug 06, 2009 | Heating & Cooling
May 03, 2009 | Carrier Heating & Cooling
Apr 27, 2009 | Heating & Cooling
Mar 28, 2009 | Goodman GMS90703BXA Heater
Jan 26, 2009 | Goodman GMS90703BXA Heater
Nov 24, 2008 | Pool & Spa
281 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: