Question about Refrigerators
I have a 13-year old Whirlpool ET20TK that tripped maybe 2x in a couple of years about 8 years ago. I replaced the circuit breaker (20amp) back then and everything was fine, until mid-2008 when it tripped again. The fridge has since been tripping the breaker more frequently: Nov 2008, mid-Jan 2009, mid-Feb, and today, March 1st. The fridge is on the same circuit as the toaster/broiler and the microwave. The tripping now happens even when there's no activity on those 2 appliances - though they're plugged in.
Should I replace the circuit breaker again or just replace the fridge? Please help! Thanks in advance!
Get an inexpensive clamp amp meter (Harbor Freight has them). Turn off power to the plug. Remove plug from wall but do not disconnet wires. turn fridge OFF. plug the unit in the recept. turn on the power. set the meter for the higest reading (amps) & clamp it around the black wire. turn the fridge ON & observe start up current & the "run" current. If the fridge is within limits on the data plate the problem is in the wiring circuit, maybe a loose connection either @ the plug or the breaker. if there are several plugs in the circuit, the problem could be in one of them. In addition, if there is a gfi plug in this circuit, it could be faulty also.
Posted on Mar 02, 2009
Your fridge should draw no more than 5amp. Presuming your breaker is at least 15amp there's a problem. Move to a different circuit first. If the condition persists check the start relay on the compressor. I have a suspicion the circuit may have another item you are not aware of.
Posted on Mar 01, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 09, 2009 | Sub-Zero 30.1 cu. ft. Cabinet Depth...
Jul 10, 2009 | Whirlpool ES5FHAXS Side by Side...
Jul 05, 2009 | Spa Parts Plus GFCI, Circuit Breaker, 40...
May 02, 2009 | Beckett Corporation Beckett Professional...
Mar 01, 2009 | Whirlpool GS6NBEXR Side by Side...
Dec 15, 2008 | Ace Hardware Hi-Tech Circuit Detective...
Sep 07, 2008 | Whirlpool Refrigerators
May 31, 2007 | Frigidaire FRT15G4B Top Freezer...
1,424 people viewed this question
Usually answered in minutes!